Honeywell 1361 Install Guide
Honeywell 1361 Transformer Wiring for a Shared Installation
For Online Support visit: http://www.security.honeywell.com/hsc/resources/MyWebTech/
INTRODUCTION: This guide shows how to wire the Honeywell 1361 Transformer (16.5VAC, 40VA) when it is desired to power both the control panel and the GSMV or IGSMV Communications Module from one transformer. IMPORTANT: ! You must use the Honeywell 1361 Transformer. ! This configuration ONLY applies to the VISTA-10P, VISTA-15P, VISTA-20P control panels when used with the GSMV or IGSMV Communications Module. ! DO NOT use this configuration with any other control panel. ! DO NOT use this configuration if using two-way voice. ! This configuration has not been evaluated by UL. To wire the transformer, perform the following steps: 1. If the control panel and/or communications module is already powered, remove AC power, then disconnect the battery on each unit. 2. Wire the Honeywell 1361 Transformer as shown below.
1361 TRANSFORMER 30 FT. MAX TO MODULE 18 AWG. WIRE (MIN) TO 110 VAC UNSWITCHED OUTLET
3. At the control panel, plug the transformer in. 4. Reconnect the battery at the control panel and the communications module.
WARRANTY: For the latest warranty information go to: http://www.security.honeywell.com/hsc/resources/wa/
2 Corporate Center Drive, Suite 100 P.O. Box 9040, Melville, NY 11747 Copyright " 2011 Honeywell International Inc. www.honeywell.com/security
800-08251 2/11 Rev. A