Honeywell 6148 Installation manual
K5320V2 4/04 Rev. A
ADEMCO 6148 Remote Keypad
INSTALLATION AND SETUP GUIDE
The ADEMCO 6148 is an addressable remote keypad designed for use with ADEMCO control panels. Addresses are set via the keypad keys. The keys on the keypads are continuously backlit for convenience.
KEYPAD DISPLAY AND LEDS
The ADEMCO 6148 keypad has a fixed-word display and a 2digit zone identifier. The following table describes the LEDs and their functions:
Red (ARMED) Green (READY) Lights when the system is armed in any mode. Lights when the system is "ready" to be armed.
NOTE: TO REMOVE CASE BACK PUSH IN THE TWO MOUNTING SNAPS LOCATED ALONG THE BOTTOM OF THE KEYPAD AND LIFT UP.
SPECIAL-FUNCTION KEY PAIRS
The keypad also features special-function key pairs. These key pairs may be used to activate panic alarms. See the control's instructions for details. Key pairs activate immediately. The following key pairs are used by the ADEMCO 6148 to manually activate silent emergency, audible emergency, personal emergency, or fire alarms: • • •  & [✱] [✱] & [#]  & [#]
SETTING THE KEYPAD ADDRESS
The keypad can be set either for an address of 00-30, or to the non-addressable mode (31). The keypad's default address is 31. Refer to the Installation and Setup Guide of the control panel being used for correct address settings and other details. To change the keypad's address, do the following: 1. Power up the keypad. Within 60 seconds of power-up, press and hold down the  and  keys at the same time for 3 seconds. (If unable to enter address mode, power up and try again.) The current keypad address is displayed, and the cursor is under the "tens" digit. If 10 seconds have passed with no key entry, the keypad automatically exits address mode. You must power down, power up and start address mode again. NOTE: The keypad will not enter address mode if the panel to which it is connected is in programming mode. 2. Set the current address to "00": Press  to clear the current "tens" digit. The cursor moves to the "ones" digit position. Press  to clear the current "ones" digit. The cursor moves back to the "tens" digit position. 3. Enter the keypad's address: Enter the proper "tens" digit of the keypad's address. The cursor moves to the "ones" digit position. Enter the proper "ones" digit of the keypad's address. Note that address "31" sets the keypad to nonaddressable mode. 4. Exit address mode: Press [✱] to save the displayed address and exit address mode.
WIRING AND INSTALLATION
The keypads can be surface mounted directly to a wall, or to a single- or double-gang electrical box. 1. Remove the case back by pushing down two "snaps." See diagram that follows. 2. 3. 4. Route wiring from the control panel through the opening in the case back. Mount the case back to a wall or electrical box. Wire directly from the keypad’s terminal block to the terminal block on the control board. See Wirng Table that follows.
Keypad ÎG – + ÏY Wiring Table Control Panel Data In – Aux Pwr (GND) + Aux. Pwr Data Out Wire Color Green Black Red Yellow
VIEWING THE KEYPAD ADDRESS
Press and hold down the  and  keys at the same time for about 3 seconds. The current address is displayed. No key entry is allowed. Press any key to exit, or wait 10 seconds to automatically exit viewing mode.
5. Reattach the keypad to its case back.
Physical: 4-1/4"H x 5-5/8"W x 1"D Display: Fixed-Word LCD. Sounder: Piezo-electric (fire alarm is loud, pulsing single tone; burglary alarm is loud, continuous, dual tone). Voltage: 12VDC Current: 55mA…sounder on, 30mA…standby, alarm sounder off.
REFER TO INSTALLATION INSTRUCTIONS FOR THE CONTROL PANEL WITH WHICH THIS DEVICE IS USED FOR WARRANTY INFORMATION AND LIMITATIONS OF THE ENTIRE ALARM SYSTEM.
165 Eileen Way, Syosset, New York 11791
Copyright © 2004 Honeywell International Inc. www.honeywell.com/security
K5320V2 4/04 Rev. A