Honeywell Home PROSIXFLOOD Installation Instructions - Dated 2/19 Rev. C
and Setup Guide
is a wireless flood sensor with
external probe (FP280) intended for use with Honeywell
controls that support
SiX™ series devices.
When the probe contacts water, the sensor sends an
alarm or trouble signal
to the controller depending on
zone type selected (ex. trouble
= Monitor Zone; alarm
within 15 seconds*
. The probe is supervised
for an open circuit (cut wire) and sends a trouble signal
up to 15
after the condition is sensed. The
sensor also has a front cover tamper and wall tamper
* See Controller’s instructions for setting alarm delay
options, if available.
MOUNT THE PROSIXFLOOD
1. Open the case
- firmly s
lide the front
housings in opposite directions and
2. Mount the
to a wall as shown,
the double sided tape and screws provided.
3. Connect the flood probe’s wires to the
4. Mount the flood probe in the area where flood
notification is desired.
Secure probe with #6 x ¾” pan
head screw provided.
5. Reattach front cover and s
ecure with the #2
and before mounting, verify adequate
signal strength by conducting a sensor test
controller’s instructions) with the devic
e in its intended
mounting location. Adjust the device location and
orientation as necessary.
= Terminal Blo
ck for sensor
= Tamper S
ENROLL AND SETUP
in Programming Mode
to activate the
(Use the tamper switch
if the battery tab is removed.)
2. The LED flashes (
up to about 20 seconds*) during
The device sends its unique MAC ID (Serial
ler registers the device and
the transmitter data on screen
Enrollment time varies depending on the
signal strength between the device and the
the LED is ON for 3 seconds and the
: If the device is not s
during the enrollment period, the LED turns off
and the device powers down. Activate the
switch to restart the enrollment
: Once enrolled in a system, the
cannot be used with another controller
it is removed from the current controller. See the
Controller’s instructions for details.
: After enrollment, the unit can be tested
by placing the probe in a cup of water. The control sh
indicate a fault condition after 15 seconds.
HOUR ENROLLMENT DELETION AND
If the device is enrolled in a panel different than the
intended panel, and you are unable to delete it from
the unintended panel, reset
1. Open the cover
and remove the battery.
wn the tamper switch while reinserting the
Rapid LED flashing indicates successful
deletion (LED flashes as if in enrollment mode). If
LED does not flash, delete was not successful.
3. Reattach the cover.
This procedure is available for 24 hours
enrollment with a panel and the device remains
powered (battery installed).
Rapid Flashes for
about 20 seconds, then
ON for 3 seconds
Power Up –
Power Up –
per activated. To stop
clear the tamper condition
reattaching the cover
. It also
out after 10 minutes.
(while in Programming Mode)
Sensor LED toggles on and off when the sensor is selecte
d. See Sensor
Push the bottom latch of the mounting
bracket back to disengage
the back housing, up and out to remove
it from the
Slide the front and back housings in
ll the housings
then insert a new battery
Place the front and back housings
together and slide them together as
: Risk of fir
and burns. Do not recharge, disassemble, heat
or incinerate. Dispose of
used batteries proper
ly. Keep away from
: Constant exposure to high or low
temperature or high humidity may reduce
atteries specified in marking. Use of a different battery
may have a detrimental effect on product operation.
1 x 3V Lithium, Resideo
Duracell DL123A or Huiderui CR123A
– 122° F / 0°
– 50° C
(Agency Compliance 32°
– 120° F / 0°
– 49° C)
95% max. (Agency Compliance -
1” H x 3.13” L x 1.61” W / 25.
5 mm H x 79.5 mm L x 41 mm
FCC / IC
Conforms to ANSI/
Certified to CAN/CSA STD C22.2
Product must be tested at
least once each year
FEDERAL COMMUNICATIONS COMMISSION &
The user shall not make any changes or modifications to the equipment unless authorized by the Installation Instructions or User's Manual. Unauthorized changes or modifications could void the user's
authority to operate the equipment.
S B DIGI
TAL DEVICE STATEMENT
This equipment has been tested to FCC requirements and has been found acceptable for use. The FCC requires the following stat
ement for your information: This equipment generates and uses radio
frequency energy and if not insta
used properly, that
is, in strict accordance with the manufacturer's instructions, may cause interference to radio and television reception. It has been type tested
and found to comply with the limits for a Class B computing device in accordance w
specifications in Part 15 of FCC Rules, which are designed to provide reasonable protection against such
interference in a residential installation. However, there is no guarantee that interference will not occur in a particular i
nstallation. If th
is equipment does cause interference to radio or television reception,
which can be determined by turning the equipment off and on, the user is encouraged to try to correct the interference by one
or more of the following measures:
If using an indoor ant
replace it with a qual
ity outdoor antenna.
Reorient the receiving antenna until interference is reduced or eliminated.
Move the radio or television receiver away from the receiver/control.
Move the antenna leads away from any wire runs to the receive
Plug the receiver
/control into a different outlet so that it and the radio or television receiver are on different branch circuits.
Consult the dealer or an experienced radio/TV technician for help.
CLASS B STATEMENT
This Class B digital ap
complies with Canadi
Cet appareil numérique de la classe B est conforme à la norme NMB
-003 du Canada.
FCC / I
This device complies with Part 15 of the FCC Rules, and I
s. Operation is subject to the f
two conditions: (1)
This device may not cause harmful interference, and (2)
This device must accept any interference received, including interference that may cause undesired operation.
Cet appareil est conforme à la partie 15 des règles de la FCC
pt de licence RSS d’
. Son fonctionnement est soumis aux conditions suivantes: (1) Cet appareil ne doit pas causer
d’interférences nuisibles. (2) Cet appareil doit accepter toute interférence reçue y compris les interférences causant une r
Party / Issuer of Supplier’s Declaration of Conformity: Ademco Inc., a subsidiary of Resideo Technologies, Inc., 2 Corporate Center Drive.,
Melville, NY 11747, Ph: 516-
– The antenna(s) used for thi
must be installed t
o provide a separation distance of at least 7.8 inches (20 cm) from all
persons and must not be co-
located or operating in conjunction with any other antenna or transmitter except in accordance with FCC
Mise en Garde
Exposition aux Fréquences
La/les antenne(s) utilisée(s) pour cet émetteur doit/doivent être installée(s) à une distance de
séparation d'au moins 20 cm (7,8 pouces) de toute personne et ne pas être située(s) ni fo
nctionner parallèlement à tout autre
transmetteur ou antenne, excepté en conformité avec les procédures de produit multi transmetteur FCC et ISED
REFER TO THE INSTALLATION INSTRUCTIONS FOR THE CONTROL WITH WHICH THIS DEVICE IS USED, F
IONS OF THE ENTIRE ALARM SYSTEM.
Responsible Party / Issuer of Supplier’s Declaration of Conformity: Ademco Inc., a subsidiary of Resideo Technologies, Inc., 2 Corporate Center Drive.,
Melville, NY 11747, Ph: 516-
The product should not
posed of with other
household waste. Check for the nearest authorized collection centers or authorized recyclers. The
correct disposal of end-
of-life equipment will help prevent potential negative consequences for the environment and human health.
mpt to reverse-
engineer this device by decoding proprietary protocols, de-
compiling firmware, or any similar actions is strictly prohibited.
T & WARRANTY INFORMATION
For the latest documentation
support, please go to:
For the latest warranty information, please go to:
The Honeywell Home Trademark is used under l
icense from Honeyw
is product is manufactured by Resideo
and its affiliates.
2 Corporate Center Drive, Suite 100
P.O. Box 9040, Melville, NY 11747
Resideo Technologies, Inc.