Resideo LTE-X Series - Quick Install Guide Dated 10/17
s – LTE
Quick Installation Guide
-X Series Installation and Setup Guide 800-23340 10/17.)
ries Communicator easily connects to your security system's control panel and sends alarms and messages
to AlarmNet for subsequent transfer to the central monitoring station. Th
can be mounted directly on the
control panel or remotely.
This guide addresses a simple installation using default programming values where possible. For detailed
information, refer to the LTE
-X Series Communicator Installation and Setup Guide
. Due to Honeywell's continuing
effort to improve our products, your device may look slightly different than pictured.
requires an AlarmNet account. For new installations, please obtain the account information from the
central station prior to programming the communicator
is for control panels that support ECP communications bus.
The control panel treats the communicator as an ECP device, so ensure to program the control panel with the
communicator’s device address
is for indoor use only. Standby current is
25mA, and Transmit Current is 250mA.
Honeywell offers secure web based services that enable users to remotely monitor and control their security system. These web services enable
users to: monitor and control their security system from a website, receive email and text message notifications of system events, and use text
messages to control the system and receive confirmations.
Dealers can enroll their customers for "Remote Services" by using the AlarmNet 360
e enabled, the specific programming fields
associated with these features can be programmed into the communications device either remotely using the AlarmNet 360
website or locally using
the 7720P programming tool.
1. Mount and Wire the
SELECT A MOUNTING LOCATION
When choosing a suitable mounting location, understand that it must
be mounted indoors
, and for best signal strength it should be
. Signal strength is very important for proper
operation. For most installations,
mounting the unit on the control
panel provides adequate signal strength and we suggest that this
method is tried first (especially if the control panel is not in a
basement location or in an area that contains large metal objects).
If the control panel location does not provide adequate signal
strength, then the communicator
can be mounted remotely.
VERIFY SATISFACTORY SIGNAL STRENGTH
This procedure checks
for satisfactory signal strength at the
. You can temporarily power the communicator
12V battery or from the control panel's AUX PWR terminals. In
buildings where reception may be a problem, powering from a battery
would allow the communicator
to be portable. The following
procedure assumes the control panel will be used for power.
Ensure power to the control panel (both AC and battery) is off.
Open the enclosure and connect the ECP cable connector to the
. Connect the cable
to the control’s ECP
Turn power on and wait for the communicator
Position the communicator
near a suitable mounting position.
Verify the Signal Strength LED (green)
Verify the signal strength remains steady for a few minutes, then
mark that mounting position. Turn power off.
Initial Power Up
initial power up, the communicator LEDs blink in
sequence from top to bottom
This sequence may take up to 15 minutes.
Do not res
et power during this
final stages of initialization
REG LED lights solid while
FAULT LED lights solid on or flashes rapidly (if module not
connected to the control panel
initialization is complete,
AL LED lights solid (the yellow
and red LEDs may also blink, per their
After initial network setup, subsequent resets or power ups can take up to 90
MOUNT THE COMMUNICATOR ON THE CONTROL PANEL
Ensure power to the control panel (both AC and battery) is off, then
remove a knockout on the top right.
Open the cover and remove the bottom knockout for the threaded mount.
Remove the Hole Cap attached to the plastic, and snap it into the top of
Install the thread
ed mount so it snaps into the plastic retaining tabs.
Mount the communicator
i n the cabinet's knockout, and fasten with the
Connect the ECP cable to the communicator’s
circuit board and thread
the wires through the threaded mounting adapter.
: Although mounting the communicator
on the control panel is preferred, it may
also be wall mounted. When wall mounting, please follow these guidelines:
Use both mounting holes to fasten.
Route the wiring through the communicator
's rear or bottom wiring access hole.
Ensure all wiring splices are located within the communicator’
Secure all wiring with ties as necessary.
Follow the recommended wire gauge sizes.
Minimum Wire Gauge
Distance from Control Panel
75 ft (23m)
170 ft (52m)
270 ft (82m)
2. Program and Register the
You can quickly program and register the communicator by using the
website, using the 7720P Program
, or by phone.
In addition, after you program the communicator, you can register it by
using the Test Message
Using the AlarmNet
website to program and register
Refer to the online help file to program the new device.
Register the communicator.
Using the 7720P
to program and register
This procedure will program the communicator
for basic control panel
communications. For advanced features and remote services refer to
Installation and Setup
Ensure the system is powered up
and connect the programming tool to
Accept all default settings except
the following prompts which need to
be answered. Then exit the programming mode.
NOTE: Account information is provided by the central st
ation. Enter this
information in prompts 12, 13 and 14.
Primary City ID
Enter the 2
-digit primary city ID,
Primary CS ID
Enter the 2
-digit primary central station
ID number, 01
Enter the 4
-digit subscriber account
Press the [space] key to scroll through
: Must be 24 hour for compliance
registration feature allows the installer to register the
communicator through a series of keyboard commands on the 7720P
Programming Tool. This method of registration lets the installer monitor
the registration process.
Once the programming is complete, press the
[Shift] plus the up arrow
key on the 7720P.
The registration message is sent and the unit
waits for the acknowledgment.
If this is a new installation and the city, central
station, and customer num
bers have been
correctly entered, the communicator
and this message is displayed.
is now in full service and
available for alarm reporting to the central station.
Using the Test Message
After programming, i
nitiate the registration sequence by
Test Message / Registration switch
Power has been supplied to the microcontroller
Using the Phone to program and register
You can program and register th
e communicator by calling the
AlarmNet Support at 1-
-6525 (Option 1). (Monday
am to 9:00 pm, Saturday 9:00 am to 5:30 pm EST) You will need the
MAC ID and CRC (located on the box and inside the communicator).
bscriber information (provided by the central station), including a
city code, CSID, and subscriber ID.
When Instructed to do so, triple click the TEST MESSAGE
– The antenna(s) used for this device must be ins
talled to provide a
separation distance of at least 7.8 inches (20 cm) from all persons and must not
-located or operating in conjunction with any other antenna or transmitter
except in accordance with FCC and ISED multi
-transmitter product procedures
Mise en Garde
Exposition aux Fréquences
La/les antenne(s) utilisée(s) pour cet
émetteur doit/doivent être installée(s) à une distance de séparation d'au moins
20 cm (7,8 pouces) de toute personne et ne pas être située(s) ni fonctionner
ent à tout autre transmetteur ou antenne, excepté en conformité avec
les procédures de produit multi transmetteur FCC et ISED.
Important Note About External Antennas
If an external cellular radio antenna is used, the antenna may be
talled or replaced ONLY by a professional installer.
To the Installer
-XV: The external antenna gain shall not exceed 6.94 dBi for 700
MHz, 6.00 dBi for 1700 MHz, 9.01 dBi for 1900 MHz
: The external antenna gain shall not exceed 6.63 dBi
for 700MHz & 850MHz, 6 dBi for 1700MHz and 8.51 dBi for
DOCUMENTATION AND ONLINE SUPPORT
FOR PATENT INFORMATION,
7 Rev B
2 Corporate Center Drive, Suite 100
P.O. Box 9040, Melville, NY 11747
7 Honeywell International Inc.