DSC AMP-702 - Installation Manual
FCC COMPLIANCE STATEMENT
CAUTION: Changes or modifications not expressly approved by Digital Security Controls Ltd. could void your
authority to use this equipment.
This equipment generates and uses radio frequency energy and if not installed and used properly, in strict accordance with the
manufacturer’s instructions, may cause interference to radio and television reception. It has been type tested and found to com
with the limits for Class B device in accordance with the specifications in Subpart “B” of Part 15 of FCC Rules, which are desi
to provide reasonable protection against such interference in any residential installation. However, there is no guarantee that
interference will not occur in a particular installation. If this equipment does cause interference to television or radio rece
can be determined by turning the equipment off and on, the user is encouraged to try to correct the interference by one or more
Re-orient the receiving antenna
Relocate the alarm control with respect to the receiver
Move the alarm control away from the receiver
Connect the alarm control into a different outlet so that alarm control and receiver are on different circuits.
If necessary, the user should consult the dealer or an experienced radio/television technician for additional suggestions. The
find the following booklet prepared by the FCC helpful: “How to Identify and Resolve Radio/Television Interference Problems”.
This booklet is available from the U.S. Government Printing Office, Washington, D.C. 20402, Stock # 004-000-00345-4.
©2000 Digital Security Controls Ltd.
1-800-387-3630 • www.dscgrp.com
Printed in Canada 29003565 R002
Digital Security Controls Ltd. warrants that for a period of twelve months from the date of purchase, the product shall
be free of defects in material and workmanship under normal use and that in fulfillment of any breach of such warranty,
Digital Security Controls Ltd. shall, at its option, repair or replace the defective equipment upon return of the equipment
to its repair depot. This warranty applies only to defects in parts and workmanship and not to damage incurred in
shipping or handling, or damage due to causes beyond control of Digital Security Controls Ltd. such as lightning,
excessive voltage, mechanical shock, water damage, or damage arising out of abuse, alteration or improper
application of the equipment.
The foregoing warranty shall apply only to the original buyer, and is and shall be in lieu of any and all other warranties,
whether express or implied and of all other obligations or liabilities on the part of Digital Security Controls Ltd. This
warranty contains the entire warranty. Digital Security Controls Ltd. neither assumes, nor authorizes any other person
purporting to act on its behalf to modify or to change this warranty, nor to assume for it any other warranty or liability
concerning this product.
In no event shall Digital Security Controls Ltd. be liable for any direct , indirect or consequential damages, loss of
anticipated profits, loss of time or any other losses incurred by the buyer in connection with the purchase, installation
or operation or failure of this product.
Digital Security Controls Ltd. recommends that the entire system be completely tested on a regular basis. However,
despite frequent testing, and due to but not limited to, criminal tampering or electrical disruption, it is possible for this
product to fail to perform as expected.
The AMP-702 contact uses a 2-wire connection for power and to communicate
with the control panel. This simplifies wiring and reduces installation cost. The
AMP-702’s low current draw also maximizes the number of devices that can be
attached to an addressable loop.
The AMP-702 has a single EOL5.6KW supervised loop that monitors normally open
contacts only. An open on the loop initiates a trouble and a short initiates an alarm.
The AMP-702 contains an internal tamper switch to monitor tamper conditions.
In Alarm current
0°C - 49°C (32°F - 120°F)
5% - 95% RH, non-condensing
Size (H x W x D)
................................................ 27 x 85 x
19mm / 1
Control Panel Compatibility
PC4010(CF) / 4020(CF) v3.0
PC5010/5015 v2.X with PC5100 interface module
Run the connection wires through the wiring holes on the back of the unit.
To mount the unit , secure the base of the unit to a UL
Listed 4 inch octagon box or equivalent UL Listed
enclosure. Remove the plastic cover and attach to
the inside of box with screws, UL Listed double
sided tape or the equivalent. The open contact to be
monitored should be wired as shown in the connection
diagram. The plastic cover is to be reattached to
permit the tamper switch to electrically supervise the
plastic cover. All wiring to and from the UL Listed
enclosure is to meet NFPA 72 and NFPA 70 Article when used in connection to Fire Alarm
Installations. When mounted in a non-fire application the AMP-702 may be mounted directly
to the surface desired without need of additional enclosure or conduit.
To mount the unit , secure the base of the unit to a cUL Listed or CSA certified 4 inch
octagon box or equivalent Listed enclosure. Remove the plastic cover and attach to the
inside of box with screws, or the equivalent (double sided tape is not permitted). The
open contact to be monitored should be wired as shown in the connection diagram. The
plastic cover is to be reattached to permit the tamper switch to electrically supervise
the plastic cover. All wiring to and from the cUL Listed or CSA certified enclosure is to
meet NFPA 72, ULC ORD C693 and Canadian Electrical Code Section 32 when used
in connection to Central Station Fire Installations. When mounted in a non-fire application
the AMP-702 may be mounted directly to the surface desired without need of additional
enclosure or conduit.
Addressable Fire Point Module
CSA certified, cUL Listed,
UL Listed 4" octagon box with
cover or equivalent
For UL Fire Installations,
use UL Listed enclosure
For ULC Fire Installations, use
cUL Listed or CSA certified enclosure
The serial number located on the back of the device must be enrolled into the alarm
control panel via Installer’s Programming ([
]  [Installer’s Code]). This procedure is
outlined for the PC4010/4020 v3.0 in the control panel Installation Manual and for the
/5015 v2.X in
the PC5100 Installation Manual.
WARNING: Connect only DSC Addressable Series devices to the addressable loop
connections. Connection of ANY other type of device will impair operation. Any
devices other than Addressable Series devices which require power to operate
must be powered separately.