Honeywell IS216T-CUR Installation Manual
printed circuit board (PCB).
Select the mounting location.
❷ Separate the sensor housings and remove the ❸
Mount the unit.
Corner Mount Corner Mount
Wall Mount Ceiling/Sky Light Ceiling Mount Protection
Vertical Wall Mount
2.4 m to 3.6 m (8' to 12’)
2.3 m (7.5’) 1.5 m to 2.7 m (5’ to 9’) Minimum
• Use a small screwdriver to remove the cover screw (if installed), then push in the housing latch at the bottom of the sensor, and gently pull apart the housings.
Wall Mount Wire Channel
Strain Relief Options
Mounting Location Guidelines • Mounting Height: Walls: vertical position -- 1.5 m to 2.7 m (5' to 9'); horizontal position -- 2.3 m (7.5’) minimum. Ceiling: 2.4 m to 3.6 m (8' to 12'). • Avoid direct or reflected sunlight. • Aim sensor away from windows or heating/cooling devices. • Sensor must have a clear line-of-sight to protected area. • Push outward on the PCB latch and lift the PCB out of the housing.
• Slide the wire through the wire knockouts in the back housing, attach the wire with a wire tie, and cut off the excess wire tie. • Mount the back housing flat against a wall or in a corner using #6 screws.
[Note: if using a mounting bracket (see Accessories), follow the installation instructions supplied with the bracket.] • Replace the PCB.
LED Enable/ Disable (S1) Sensitivity (S2) Alarm LED
Wire the unit. Connect wires as shown using wire size 0.8 - 1.5 mm (22 to 16 AWG). Observe proper polarity.
❺ Set the DIP switch settings (see Step 6).
❻ Configure the sensitivity and walk-test the sensor.
POWER 16 mA, 12 VDC 18 mA max
ALARM 24 VDC 30 mA TAMPER 24 VDC 30 mA
Set the sensitivity appropriate for the application (see options below), replace the front cover, and apply power to the sensor. Begin walk-test after the LED stops flashing (see LED Operation section). Walk through the detection zones, observing the sensor’s LED whenever motion is detected. The red LED shows actual alarm relay operation. The absolute range of all PIR units is subject to variation because of different types of clothing, backgrounds, and ambient temperature. For this reason, ensure that the most likely intruder routes are well within the PIR’s detection zones and that walk-testing is carried out along those routes. High Sensitivity (Pulse Count 1) NOTE: This is the recommended setting for this sensor.
Install the Look-Down Mask (black ring supplied) as shown, if desired. Mask MUST be installed for wall mount ceiling/sky light protection and ceiling mount installations.
IntelliSense® IS216T-CUR Passive Infrared Motion Sensor Installation Instructions
SWITCH 1* 2
OFF LED Disabled Low Sensitivity
ON LED Enabled High Sensitivity
(Note: Default switch settings shown in grey.) *Refer to LED Operation Section.
Low Sensitivity (Pulse Count 2) NOTE: If Pulse Count 2 is used, be sure to thoroughly walk-test the sensor.
MOUNTING LOCATION GUIDELINES DETECTION PATTERNS
VERTICAL ORIENTATION WALL MOUNT Top View
Note: TS 50131-2-2 compliant at 1.5 m to 2.3 m mounting height.
The IS216T-CUR is designed for use indoors. The sensor can be corner, wall, or bracket mounted (see Accessories section). Make sure that the sensor has a clear line-of-sight to the protected area: infrared energy cannot penetrate solid objects, and the sensor must “see” an area in order to detect a moving person. The sensor should be pointed into the room interior, and away from windows and heating/cooling sources. Additionally, the sensor should be installed on a surface where the temperature is similar to that of the area being protected and not pointed at direct or reflected sunlight.
WALL MOUNT CEILING/SKY LIGHT PROTECTION* Ceiling protection, this is NOT a pet alley application. Top View
*Look-Down MUST be disabled -Install Look-Down Mask (see Step 5). Side View
2.3 m (7.5’) Minimum Height
To Enable the alarm LED, turn switch S1 ON. To Disable the alarm LED, turn switch S1 LED Enabled LED Disabled OFF. The LED will temporarily remain enabled for 10 to 12 minutes. This feature gives the installer time to walk-test the unit as explained below. Automatic Walk-Test Mode with alarm LED disabled (switch S1 OFF): After applying power to OPERATION the sensor, it will warm Alarm LED up for up to two Conditions Alarm Relay Enabled Disabled minutes, and then the Closed Warm Up Slow Blink Slow Blink LED will temporarily remain enabled for a 10 (up to 2 min.) OFF OFF Closed Normal minute walk-test period. ON for 3 *See LED Opened Alarm After 10 minutes, the seconds Operation for 3 seconds LED will automatically See switch to disabled. Trouble Fast Blink Fast Blink Troubleshooting To restart the 10 minute walk-test mode, switch S1 ON, and then OFF again.
Note: TS 50131-2-2 compliant at a minimum mounting height of 2.3 m (7.5’).
Range: 10 m (33') in Vertical Wall Mount Orientation Mounting Height: Walls: Vertical - 1.5 m to 2.7 m (5' to 9'); Horizontal - 2.3 m (7.5’) minimum Ceiling: 2.4 m to 3.6 m (8' to 12') Power requirements: 8.5 - 15.4 VDC (UL: 10-14 VDC); 16 mA nominal at 12 VDC, 18 mA max; AC Ripple: 50 to 120 Hz; 3 V peak-to-peak at nominal 12 VDC Alarm relay: Form A (normally closed) 30 mA, 24 VDC max., 40 Ohms resistance max Tamper switch Form A (normally closed with cover installed) 30 mA, 24 VDC RFI immunity: 30 V/m; 10 MHz - 1000 MHz PIR White light immunity: 6,500 Lux (min.) Sensitivity: Switch selectable (low & high) Operating temperature: -10o C to +55o C (14° F to 131° F) (For indoor use environment) Relative humidity: 5% to 95% non-condensing Temperature Compensation: Advanced dual slope PIR fields-of-view: dual element, 18 detection zones 4 look-down (when used)
Dimensions: 8.57 cm x 6.03 cm x 3.81 cm (3-3/8" H x 2-3/8" W x 1-1/2" D) Weight: 66.62 g (2.35 oz) Packaged Product: 89.0 g (3.13 oz) Accessories Included: Look-down mask Accessories Available: SMB-10 Swivel Mount Bracket (P/N 0-000-110-01) SMB-10C Swivel Mount Ceiling Bracket (P/N 0-000-111-01) SMB-10T Swivel Mount Bracket w/Tamper (P/N 0-000-155-01) EN 50131-1 Compliant Accessories: SMB-10T Swivel Mount Bracket w/Tamper (P/N 0-000-155-01) Approvals/listings: FCC part 15, Class B verified IC, ICES-003, Class B verified CE C-Tick cULus listed Tested and certified to prEN 50131-1:2004 and TS 50131-2-2: 2004 Security Grade 2, Environmental Class II by Telefication B.V. Note: In TS 50131-2-2 compliant installations: mount the sensor at the appropriate mounting height for the installation (see notes in Detection Patterns section at left), select the high sensitivity setting, and install a cover screw (included). Suitable for connection to an EN 60950 Class II Limited Power Source in European installations.
SIDEWAY ORIENTATION CEILING MOUNT* Top View
To obtain applicable EU compliance Declaration of Conformities for this product, please refer to our Website, http:// www.security.honeywell.com/hsce/international/ index.html. For any additional information regarding the compliance of this product to any EU specific requirements, please contact:
Quality Assurance Department, Honeywell Security & Custom Electronics, Newhouse Industrial Estate Motherwell, Lanarkshire ML1 5SB, Scotland, United Kingdom. Tel: +44(0)1698 738200 Email: UK64Sales@Honeywell.com
IMPORTANT: The IS216T-CUR should be tested at least once each year. For proper wiring methods, refer to the National Electrical Code NFPA 70.
IntelliSense® IS216T-CUR Passive Infrared Motion Sensor Product Information
• Symptom: Sensor is not operating. Corrective Action: Check to make sure the Power terminals are wired correctly. If the power terminals are wired correctly, and the sensor does not operate when power is applied, replace the sensor. • Symptom: Fast Blinking LED -- Trouble condition; two possible causes. 1. Temperature Compensation failure: The sensor checks temperature once every 100ms. When a Temparture Compensation failure occurs, the sensor defaults to room temperature sensitivity and continues to operate normally while signalling trouble. The trouble is stored in memory, and when the next valid alarm condition is detected, the alarm relay latches open. 2. PIR self-test failure: In the absence of PIR signals, the sensor internally checks its PIR circuit once every ten minutes. If six consecutive self-tests fail, the sensor signals trouble with its LED, and the relay latches closed. Subsequent detection of a valid PIR Signal will clear the trouble, and the relay will return to normal operation. Corrective Action: Replace the sensor.
Note: The distances in the illustrations do not represent maximum detection distances. A walk-test is required after mounting to ensure proper detection.
Note: TS 50131-2-2 compliant at 2.4 m to 3.6 m mounting height.
FCC NOTICE: This device complies with Part 15 of the FCC Rules. Operation is subject to the following two conditions: (1) This device may not cause harmful interference, and (2) this device must accept any interference received, including interference that may cause undesired operation. The user is cautioned that changes or modifications not expressly approved by Honeywell could void the user’s authority to operate this equipment. NOTE: This equipment has been tested and found to comply with the limits for a Class B digital device, pursuant to Part 15 of the FCC Rules. These limits are designed to provide reasonable protection against harmful interference in a residential installation. This equipment generates, uses and can radiate radio frequency energy and, if not installed and used in accordance with the instructions, may cause harmful interference to radio communications. However, there is no guarantee that interference will not occur in a particular installation. If this equipment does cause harmful interference to radio or television reception, which can be determined by turning the equipment off and on, the user is encouraged to try to correct the interference by one or more of the following measures: 1) Reorient or relocate the receiving antenna; 2) increase the separation between the equipment and receiver; 3) connect the equipment into an outlet on a circuit different from that to which the receiver is connected; 4) consult the dealer or an experienced radio/television technician for help. IC Notice: This Class B digital apparatus complies with the Canadian ICES-003. Cet appareil numérique de la Classe B est conforme à la norme NMB-003 du Canada.
© 2005 Honeywell International Inc. • Honeywell and IntelliSense are registered trademarks of Honeywell International Inc. All other trademarks are the properties of their respective owners. All rights reserved. Made in China 5-051-794-00 Rev C