Honeywell 4219 Install Guide - Original, Dated 5/01
N8924V1 5/01 Rev. B
Wired Zone Expander Module
INSTALLATION AND SETUP GUIDE
This module adds up to eight end-of-line resistor supervised
zones to compatible control/communicators via the control’s
The module may be mounted within the control’s cabinet (if
room permits), or remotely. If mounted remotely, there are
provisions to tamper protect the unit. Communication to
the module is supervised so that it cannot be disconnected
from the keypad wiring without detection by the control. If
the wiring is cut, a tamper alarm or signal will result, to
indicate that this device (and possibly other similarly
connected devices) has become inoperative.
Power should be disconnected
Be sure to mount the 4219 before
making any wire connections.
When the module is mounted remotely, holes on the back of
the module’s housing permit it to be mounted horizontally
or vertically. Wires can exit from the side or the breakout
on the back of its housing. For tamper protection, attach
the tamper magnet (provided) (Figure 1) to the module
inside cover. Place the tamper jumper (Figure 2) into its
lower position. Affix the connections label that accompanies
the module to the inside of the module’s cover. When the
installation is complete, put the modules cover on. The
magnet attached to the cover, positioned near the reed
switch, will cause a tamper signal to be sent to the control if
the cover is removed.
When the module is to be mounted inside the control’s
cabinet, mount it horizontally to the raised tabs at the back
of the cabinet. Insert self-tapping screws (provided) in two
adjacent raised tabs at the back of the cabinet. Leave the
heads projecting 1/8”. Hang the module on the screw heads
via two slotted holes on the back of the module’s housing.
When the module is installed in the control’s cabinet, it
need not be tamper protected. Place the tamper jumper
(Figure 2) in the upper position. Affix the connections label
that accompanies the module to the inside of the control’s
ee the control’s installation and setup guide for additional
CONNECTIONS AND SETTINGS
Make protection zone connections to the module’s 12-
position terminal block TB1. Each zone that is used must
have a 1000-ohm end-of-line resistor connected across the
end of its loop, as shown in Figure 1.
For CE installations ADEMCO N6361
EMI suppression bead is required.
Refer to the N6361 installation guide for
wire routing instructions.
1. INSERT BOTTOM TABS FIRST.
2. ENGAGE TOP WITH CLIP.
Figure 1. Tamper Magnet Installation
If a zone is not programmed, the resistor need not be used.
The method of programming each zone for the type of alarm
and reporting code to the central monitoring station varies
with the control to which the module is connected. Refer to
the Installation and Setup Guide for that control unit.
Set the DIP Switch to one of 16 addresses, as shown in
Figure 3, so the control can identify the module and
communicate with it properly. The address to be set is
determined by the particular control to be used, and the
control’s installation instructions must be consulted. As
shipped, the DIP Switch is set for an address of “0”.
Zone A can be set for fast response time of 10ms to an open
circuit, if desired, by setting position 1 of the DIP Switch to
“OFF”. As shipped, it is set to “ON” for a response time of
300ms, as shown in the table below. All of the module’s
other protection zones have a nominal response time of
Connections to the control’s keypad wiring points can be
made via 4-terminal block TB2 or the 4-pin plug (wire color
connections are the same).
6-7/16”W x 4-1/4”H x 1-1/4” D
(163mm x 108mm x 32mm)
12VDC (from control’s remote
keypad connection points)
TAMPER JUMPER POSITION
4219 IN CABINET
4-PIN CONSOLE PLUG
WITH 1000 OHM
(EACH ZONE'S MAX.
300 OHMS + EOL)
REED (TAMPER) SWITCH
FOR SETTING ADDRESS
AND ZONE A RESPONSE
FOR CE INSTALLATIONS A
BEAD IS REQUIRED.
Figure 2. Summary of Connections
4219 ADDRESS SETTINGS
ON ON ON ON
ON ON ON ON
ON ON ON ON ON ON ON ON
(WHITE AREAS DENOTE SWITCH HANDLES)
DETERMINE ZONE EXPANDER'S ADDRESS.
CONSULT CONTROL'S INSTRUCTIONS FOR ADDRESS USE.
SWITCH SETTING SHOWN SET FOR ADDRESS "0".
DETERMINES ZONE A's RESPONSE TIME:
ON = NORMAL (300MS) RESPONSE, SHOWN (AS SHIPPED).
OFF = FAST (10MS) RESPONSE TO AN OPEN.
Figure 3. DIP Switch Settings
SEE THE CONTROL PANEL’S INSTALLATION AND SETUP GUIDE FOR COMPLETE INFORMATION
REGARDING THE LIMITATIONS OF THE ENTIRE SECURITY SYSTEM.
Honeywell International Inc., 165 Eileen Way, Syosset, New York 11791, warrants its product(s) to be in
conformance with its own plans and specifications and to be free from defects in materials and workmanship
under normal use and service for 24 months from the date stamp control on the product(s) or, for product(s) not
having a date stamp, for 12 months from date of original purchase unless the installation instructions or catalog
sets forth a shorter period, in which case the shorter period shall apply. Seller's obligation shall be limited to
repairing or replacing, at its option, free of charge for materials or labor, any product(s) which is proved not in
compliance with Seller's specifications or proves defective in materials or workmanship under normal use and
service. Seller shall have no obligation under this Limited Warranty or otherwise if the product(s) is altered or
improperly repaired or serviced by anyone other than Honeywell factory service. For warranty service, return
product(s) transportation prepaid, to Honeywell Factory Service, 165 Eileen Way, Syosset, New York 11791.
THERE ARE NO WARRANTIES, EXPRESS OR IMPLIED, OF MERCHANTABILITY, OR FITNESS FOR A
PARTICULAR PURPOSE OR OTHERWISE, WHICH EXTEND BEYOND THE DESCRIPTION ON THE FACE
HEREOF. IN NO CASE SHALL SELLER BE LIABLE TO ANYONE FOR ANY CONSEQUENTIAL OR
INCIDENTAL DAMAGES FOR BREACH OF THIS OR ANY OTHER WARRANTY, EXPRESS OR IMPLIED, OR
UPON ANY OTHER BASIS OF LIABILITY WHATSOEVER, EVEN IF THE LOSS OR DAMAGE IS CAUSED BY
THE SELLER'S OWN NEGLIGENCE OR FAULT.
Seller does not represent that the product(s) it sells may not be compromised or circumvented; that the product(s)
will prevent any personal injury or property loss by burglary, robbery, fire or otherwise; or that the product(s) will in
all cases provide adequate warning or protection. Customer understands that a properly installed and maintained
alarm system may only reduce the risk of a burglary, robbery, fire
or other events occurring without providing an
alarm, but it is not insurance or a guarantee that such will not occur or that there will be no personal injury or
property loss as a result. CONSEQUENTLY, SELLER SHALL HAVE NO LIABILITY FOR ANY PERSONAL
INJURY, PROPERTY DAMAGE OR OTHER LOSS BASED ON A CLAIM THAT THE PRODUCT(S) FAILED TO
GIVE WARNING. HOWEVER, IF SELLER IS HELD LIABLE, WHETHER DIRECTLY OR INDIRECTLY, FOR
ANY LOSS OR DAMAGE ARISING UNDER THIS LIMITED WARRANTY OR OTHERWISE, REGARDLESS OF
CAUSE OR ORIGIN, SELLER'S MAXIMUM LIABILITY SHALL NOT IN ANY CASE EXCEED THE PURCHASE
PRICE OF THE PRODUCT(S), WHICH SHALL BE THE COMPLETE AND EXCLUSIVE REMEDY AGAINST
This warranty replaces any previous warranties and is the only warranty made by Seller on this product(s). No
increase or alteration, written or verbal, of the obligations of this Limited Warranty is authorized.
FEDERAL COMMUNICATIONS COMMISSION (FCC) Part 15 STATEMENT
This equipment has been tested to FCC requirements and has been found acceptable for use. The FCC requires the following
statement for your information:
This equipment generates and uses radio frequency energy and if not installed and used properly, that is, in strict accordance
with the manufacture’s instructions, may cause interference to radio and television reception. It has been type tested and fou
to comply with the limits for Class B computing device in accordance with the specifications in Part 15 of FCC Rules, which are
designed to provide reasonable protection against such interference in a residential installation. However, there is no guaran
that interference will not occur in a particular installation. If this equipment does cause interference to radio or televisio
reception, which can be determined by turning the equipment off and on, the user is encouraged to try to correct the interferen
by one or more of the following measures:
If using an indoor antenna, have a quality outdoor antenna installed.
Reorient the receiving antenna until interference is reduced or eliminated.
Move the radio or television receiver away from the receiver/control.
Move the antenna leads away from any wire runs to the receiver/control.
Plug the receiver/control into a different outlet so that it and the radio or television receiver are on different branch circu
If necessary, the user should consult the dealer or an experienced radio/television technician for additional suggestions. The
user or master may find the following booklet prepared by the Federal Communications Commission helpful:
This booklet is available from the U.S. Government Printing Office, Washington, DC 20402.
The user shall not make any changes or modifications to the equipment unless authorized by the Installation Instructions or
User’s Manual. Unauthorized changes or modifications could void the user’s authority to operate the equipment.
165 Eileen Way, Syosset, NY 11791
2004 Honeywell International Inc.
N8924V1 5/01 Rev. B