Honeywell 6150 (K4392V2-H M7240) and 6160 (K4274B1-H M7274) Installation Manual
K3590-ADV5 9/10 Rev. A
ADEMCO 6150 & 6160
INSTALLATION AND SETUP GUIDE
Keypad Features Backlit Display Dedicated Function Keys Built-in Sounder Piezo Speaker ADEMCO 6150 Fixed-Word (see note) ADEMCO 6160 2-Line Alpha (see note)
Note: Permanent display backlighting is an option on some controls (see the control's instructions for details).
The ADEMCO 6150 and ADEMCO 6160 are addressable Remote Keypads designed for use with ADEMCO control panels. Addresses are set via the keypad keys. The keys on the keypads are continuously backlit for convenience. Supervised by control panel (if supported).
WIRING AND INSTALLATION
The keypads can be surface mounted directly to a drywall, or to a single- or double-gang electrical box. 1. Push the two case release snaps at the bottom of the keypad with the blade of a medium screwdriver (this will push in the release snap), then pull that side of the case back away. Insert the screwdriver in the side of the keypad (between the front and back case) and gently twist to release the side locking tab. Repeat for the other side. Refer to Figure 1 for location of the case back release snaps and locking tabs. 2. Route wiring from the control panel through the opening in the case back. 3. Mount the case back to a wall or electrical box. 4. Wire directly from the keypad’s terminal block to the terminal block on the control panel. (See Wiring Table below). NOTE: No more than one wire per terminal may be connected. If daisy-chained configuration is required, pig-tail wires together so that only one wire is terminated under the screw. Use 16-24 AWG wire only!
Wiring Table (All Keypads) Keypad Control Panel Data In Wire Color Green Black Red Yellow
For ULC installations, the VISTA-128BP/VISTA-250BP Series must be used with the ADEMCO 6160 keypad.
KEYPAD DISPLAYS AND LEDS
The keypads have the following display features:
Model 6150 6160 Fixed Word Display X X 2-line Alpha Display 2-digit Zone Identifier X X Custom Zone Descriptors
The following table shows the LEDs and their functions:
LED Red Green Function Lights when the system is armed in any mode Lights when the system is "ready" to be armed.
SPECIAL FUNCTION KEYS
The keypads also feature function keys. These keys may be programmed for panic alarms or other special functions such as macros. See the control's instructions for details.
Function keys must be held down for at least 2 seconds to activate an alarm; key pairs are activated immediately. Function Keys A or  and [✻] B or [✻] and [#] C or  and [#] D
– Aux Pwr (GND) + Aux. Pwr
See the control panel’s Installation and Setup Guide for more complete details. 5. Reattach the keypad to its case back.
FUNCTION KEY LABELS
A set of adhesive-backed labels with some typical function symbols (i.e., fire, police, personal emergency, etc.) is provided. These labels can be placed on or next to the keys to identify each key's function for the end user (as determined by the control panel's capability and programming; see the control's instructions).
NOTE: TO REMOVE CASE BACK PUSH IN THE TWO MOUNTING SNAPS LOCATED ALONG THE BOTTOM OF THE KEYPAD AND LIFT UP.
OPERATING THE KEYPAD
For operating instructions, see the User Guide for the control panel used with this keypad.
RETAINING SNAPS LOCKING TAB
Physical: 6150: 6160: Displays: 6150: 6160:
4-7/8"H x 6-1/4"W x 1"D 5-5/16"H x 7-3/8"W x 1-3/16"D
Figure 1. Removing the Case Back
SETTING THE KEYPAD ADDRESS
The keypad can either be set for an address of 00-30, or to the non-addressable mode (31). The keypad's default address is 31. To change the keypad's address, do the following: 1. Enter address mode: Power up the keypad. Within 60 seconds of power-up, press and hold down the  and  keys at the same time for 3 seconds. (If unable to enter address mode, power up and try again.) The current keypad address will be displayed, and the cursor will be under the "tens" digit. If 10 seconds have passed with no key entry, the keypad automatically exits address mode. You must power down, power up and start address mode again. NOTE: The keypad will not enter address mode if the panel to which it is connected is in programming mode. 2. Set the current address to "00": Press  to clear the current "tens" digit. The cursor will move to the "ones" digit position. Press  to clear the current "ones" digit. The cursor will move back to the "tens" digit position. 3. Enter the keypad's address: Enter the proper "tens" digit of the keypad's address. The cursor will move to the "ones" digit position. Enter the proper "ones" digit of the keypad's address. Note that address "31" sets the keypad to non-addressable mode. 4. Exit address mode: Press [ ] to save the displayed address and exit address mode. VIEWING THE KEYPAD ADDRESS Press and hold down the  and  keys at the same time for about 3 seconds. The current address is displayed. No key entry is allowed. Press any key to exit or wait 10 seconds to exit viewing mode.
Fixed-Word LCD (backlit). 2 x 16 alpha-numeric supertwist LCD, backlit.
6160: Voltage: Current: 6150:
Piezo-electric (fire alarm is loud, pulsing single tone; (all Keypads) burglary alarm is loud, continuous, dual tone). Speaker. 12VDC (power-limited)
70mA (ARMED LED lit, LCD backlight and sounder on), reduces to 40mA when panel is operating in standby mode (backlight off). 150mA (ARMED LED lit, LCD backlight and sounder on), reduces to 40mA when panel is operating in standby mode (backlight off). Compliant.
REFER TO INSTALLATION INSTRUCTIONS FOR THE CONTROL PANEL WITH WHICH THIS DEVICE IS USED FOR WARRANTY INFORMATION AND LIMITATIONS OF THE ENTIRE ALARM SYSTEM. For the latest warranty information, please go to: http://www.security.honeywell.com/hsc/resources/wa/index.html
2 Corporate Center Drive, Suite 100 P.O. Box 9040, Melville, NY 11747
Copyright © 2009 Honeywell International Inc. www.honeywell.com/security
K3590-ADV5 9/10 Rev. A