SiXSIREN Installation Guide
This wireless siren/strobe is intended for use
with Honeywell controls that support SiX™
Gently twist the top of the Siren
counterclockwise and the
mounting bracket clockwise to
This device can be enrolled and programmed either
before or after installation.
1. Set the Lyric Controller in Programming Mode and
go to Zone Programming. Select Add New, then
Serial Number. Follow the controller’s instructions
to begin enrollment.
2. Insert four 1.5V AA Lithium batteries (included) to
activate the device and begin the enrollment
3. The Green LED flashes rapidly during enrollment
(up to about 20 seconds*)
Programming Mode > Zones >
Add New > Serial Number
Zone Description 1
Zone Description 2
*NOTE: Enrollment time varies depending on the signal
strength between the device and the controller.
• The device sends its unique MAC ID address
(Serial Number) and Services information to the
• The controller registers the device and displays
the transmitter data on screen.
4. Enrollment is confirmed when the Green LED is
ON for 3 seconds and the controller chirps once.
5. Trigger the device tamper switch again to complete
enrollment and press SAVE.
6. The device did not enroll in the system if:
• The White LED flashes, the system chirps and
the device powers down.
• The Green LED flashes rapidly when the device
is removed from the mounting bracket (the
tamper switch is triggered).
To restart the enrollment process, ensure the
system is in programming mode and activate the
The device can also be manually enrolled. See the
Controller’s Programming Guide for details.
The LED Flashes; wait
up to about 20 seconds*
The Green LED
is ON for 3 seconds
Trigger the device
again to complete
After enrolling, update the SiXSIREN firmware (via the
Controller) to ensure the latest version is used. See the
NOTE: Once enrolled in a system, the device cannot be used with
another controller until it is removed from the current controller. See
the Controller’s instructions for details.
Program the SiXSIREN
Consult the Controller’s instructions for programming the device in the system. sensing –
range is 0° – 120° F (-18° – 49° C); accuracy ±3° F (1.67° C)
NOTE: Before mounting the device permanently,
conduct Go/No Go tests (see controller’s
instructions) to verify adequate signal strength and
adjust the device location and orientation as
#6 x 1”
(3.5 mm x 25 mm)
The SiXSIREN can be mounted on the wall or on
#4 x 1/4”
(2.9 mm x 6.4 mm)
The rear tamper breakout [A] MUST be mounted to
a stud, solid wood, or with a robust wall anchor.
Test the SiXSIREN
The SiXSIREN should be tested immediately after installation and weekly. Activate Test Mode remotely from the
Controller (see Controller’s manual for details). The product must be tested at least once a year.
Test Mode tests the sounder and LED:
• Sounder – the Burglary warble tone will sound for 3 seconds.
• LED – the White LED strobe will flash for 15 seconds.
SiXSIREN LEDs and Sounder
Refer to the table below for operation of the four bi-colored LEDs and an 85dB sounder.
R = Red
G = Green
W = White
= Rapid Flash
= Temporal Pulse 3
= Slow Flash
= Strobe Flash
= Burglary Warble
= Temporal Pulse 4
Red ON for 20
Alternating Red and
White Flashing Strobe
(continues until the
Alarm is cleared)
White Strobe Flashing
Red flashes once
every 45 seconds
Green Rapid Flashes for
about 20 seconds, then
ON for 3 seconds
Green Slow Flashing for
Power Up – Enrollment
Green ON for 20 seconds
Power Up – Device
System is Disarmed
System is Armed
Smoke / Heat Alarm
White Strobe Flashing
ON for 3 seconds
Green Flashes slowly for
Strobe flash = two flashes per second, then OFF for 1 second.
It is best to replace the battery BEFORE the chirping begins. Once started, the sounder continues to chirp until batteries are replaced or die. See
the Battery Replacement section.
Twist the front cover counterclockwise and separate it
from the mounting bracket.
Remove the batteries, wait 10 seconds and insert four
new batteries of the same type and brand.
Recommended replacement batteries:
- 1.5V AA Lithium Batteries [Non-Rechargeable]
- AA Alkaline batteries can be used, but battery life will
be significantly reduced.
NOTE: Do not mix old and new batteries, battery
types or manufacturers.
Reattach the front cover and twist clockwise to secure it
BATTERY CAUTION: Risk of fire, explosion and burns.
Do not recharge, disassemble, heat above 212 F (100 C) or
incinerate. Dispose of used batteries properly. Keep away from
1.5V, AA Lithium
Range: 300 feet nominal indoors (actual range determined by the system in TEST mode)
Battery: Four 1.5V, AA Lithium, Non-Rechargeable; Energizer E , Honeywell 462
Tamper: Cover and Wall tamper
RF Frequency: 2.4GHz
Input Voltage: 3,3VDC
Current: 339 mA, Typical
Siren Output Level: 85 dB at 10 feet
Operating Temperature: 0° to 50° C / 32° to 122° F (Agency Compliance 32° to 120° F / 0° to 49° C)
Relative Humidity: 95% max. (Agency compliance – 93% max), non-condensing
Dimensions: 14.14 cm Diameter x 4.62 cm Thick / 5.5 in. Diameter x 1.8 in. Thick
Weight: xx oz (xx g)
FCC / IC
Conforms to UL 985 /
Certified to ULC-S545 &
FEDERAL COMMUNICATIONS COMMISSION & INDUSTRY CANADA STATEMENTS
The user shall not make any changes or modifications to the equipment unless authorized by the Installation Instructions or User's
Manual. Unauthorized changes or modifications could void the user's authority to operate the equipment.
FCC / IC STATEMENT
This device complies with Part 15 of the FCC Rules, and RSS-210 of Industry Canada. Operation is subject to the following two
conditions: (1) This device may not cause harmful interference, and (2) This device must accept any interference received, including
interference that may cause undesired operation.
Cet appareil est conforme à la partie 15 des règles de la FCC & de RSS-210 des Industries Canada. Son fonctionnement est soumis
aux conditions suivantes: (1) Cet appareil ne doit pas causer d’interférences nuisibles. (2) Cet appareil doit accepter toute interférence
reçue y compris les interférences causant une reception indésirable.
Warning – The antenna(s) used for this device must be installed to provide a separation distance of at least 7.8 inches (20 cm)
from all persons and must not be co-located or operating in conjunction with any other antenna or transmitter except in accordance
with FCC multi-transmitter product procedures.
MISE EN GARDE EXPOSITION AUX FREQUENCES RADIO
Attention : L'antenne (s) utilisée pour cet émetteur doit être installée à une distance de séparation d'au moins 7,8 pouces (20 cm)
de toutes les personnes.
SUPPORT & WARRANTY
REFER TO THE INSTALLATION INSTRUCTIONS FOR THE CONTROL WITH WHICH THIS DEVICE IS USED, FOR DETAILS
REGARDING LIMITATIONS OF THE ENTIRE ALARM SYSTEM.
For the latest documentation and online support information, please go to:
For the latest warranty information, please go to:
For patent information, see www.honeywell.com/patents
2014 Honeywell International Inc. Honeywell and is a registered trademark of Honeywell International Inc.
All other trademarks are the properties of their respective owners. All rights reserved.
2 Corporate Center Drive, Suite 100
P.O. Box 9040, Melville, NY 11747
800-21342 11/15 Rev A