How Do I Set Up A Hardwire Zone On Honeywell L7000?
The Honeywell Lynx Touch L7000 comes equipped with one EOLR supervised zone which supports both open and closed circuit devices. The Lynx Touch L7000 hardwire zone has a response time of 350msec and a maximum zone resistance of 300 ohms plus EOLR. The Lynx Touch L7000 hardwire zone cannot be used for a fire zone.
To set up the hardwire zone on the Lynx Touch L7000 connect the contact to the hardwire zone terminals GND (-) and HWZ1 (+). For closed circuit devices, connect in series in the high (+) side of the loop. The EOL resistor must be connected in series with the devices, following the last device. For open circuit devices, connect in parallel across the loop. The 2000-ohm must be connected across the loop at the last device.
The Honeywell Lynx Touch L7000 is an excellent choice in alarm control panels. The Lynx Touch L7000 supports a total of 104 zones, 1 hardwire and 103 wireless. The Lynx Touch L7000 also supports zwave device control when paired with a L5100zwave module. The Lynx Touch L7000 can support up to 4 thermostats and 6 door locks plus up to 40 additional zwave devices.
The Lynx Touch L7000 is also compatible with Honeywell IP cameras, when paired with either the L5100Wifi module or an ILP5 internet communicator a user can view up to 4 right on the touchscreen.
The Lynx Touch L7000 is also compatible with Total Connect 2.0 when paired with either the Honeywell 4GL, L5100Wifi module or the ILP5 internet communicator.
Total Connect 2.0 allows users to control an alarm system, home automation and Honeywell IP cameras from any computer, smartphone or ios device. A user will also receive notifications via email and or text messages on alarm events.
Did you find this answer useful?
We offer alarm monitoring as low as $10 / monthClick Here to Learn More