Alarm Grid Video Recap: July 30th - August 2ndPosted By Michael Goris
Hi DIYers! It's time for our weekly video recap. We have a great batch of videos for you all today. Our technicians Joe, Jarrett, and Jorge will all help you learn how to use your alarm systems and get the most out of your equipment. Let's check out the latest videos from the team.
Joe teaches users how to add wired motion detection sensors to a Resideo VISTA 20P System. Hardwired motion sensors will use a 4-wire connection, with two (2) wires being used for the zone input, and two (2) wires being used for power. Most hardwired motion sensors use a Normally Closed (NC) wiring configuration, meaning that they are wired in Series. However, there are some Form C motion sensors that can use a Normally Open (NO) wiring configuration for wiring in parallel.
Joe explains how to troubleshoot a low battery condition on a Resideo VISTA Alarm Panel. You will need a voltmeter to do this. The first step is to check the AC voltage. You should expect to see about 18 to 19 volts on a 16.5VAC transformer. Next, check the Auxiliary Power. You should see a reading of 13 volts or higher. Finally, you should check the charging voltage. This should be the same as the auxiliary power voltage.
Joe teaches users how to add 2-wire smoke detectors to a Qolsys Hardwire 16-F. Any 2-wire smoke detectors used with the Hardwire 16-F must be connected at Zone 16. You must wire the smoke detector(s), plus any other sensors used with the module, before enrolling the Hardwire 16-F with the panel. This lets the module know the proper configuration for each zone. The 2-wire smoke detectors will use Normally Open (NO) wiring. Most burglary devices use Normally Closed (NC) wiring. CO detectors cannot be used with the Hardwire 16-F. You will also need 4.7k resistors at each zone.
Jorge explains how you cannot turn off the Arm Confirm feature on a Qolsys IQ Panel 2 Plus System. The Arm Confirm feature has the panel produce a loud tone when the system is Armed Away using a key fob or wireless keypad. The purpose of this tone is to make sure that the user knows that they have set their system to Arm Away and that they should exit the premises. Unfortunately, you cannot turn off the Arm Confirm feature on the IQ Panel 2 Plus System because it does not exist.
Jarrett discusses the difference between the Arm Away and Arm Maximum modes. When you Arm Maximum, you are telling your system to ignore all of the Entry Delay Periods on your system. This means that if you open an Entry/Exit Zone while the system is set to Arm Maximum, then an immediate alarm will occur. If you are outside the building, you will need to disarm using a key fob or an interactive platform like Total Connect 2.0 or Alarm.com.