Technical Advisory Regarding PowerG Sensors and Qolsys IQ Panel 2 PlusPosted By Michael Goris
Alarm Grid has learned of technical difficulties between certain PowerG Sensors and the Qolsys IQ Panel 2 Plus. These issues affect the PG9914 Wireless Motion Sensor and the PG9933 Wireless Carbon Monoxide Sensor when used on an IQ2+ System running PowerG Version 80.17.
Due to this issue, any DSC PowerG PG9914 Wireless Motion Sensor manufactured before August 23, 2018 will not work with a Qolsys IQ Panel 2 Plus running PowerG Firmware Version 80.17. This includes any PG9914 running firmware V3.0.5 or V3.0.7. Also, if the first four (4) digits of the Serial Number are less than "3618", then the device is affected.
Below are some pictures of a PG9914 that will not work with an IQ Panel 2 Plus running PowerG Version 80.17:
Additionally, any DSC PowerG PG9933 Carbon Monoxide Sensor manufactured before March 26, 2019 will not work with a Qolsys IQ Panel 2 Plus running PowerG Firmware Version 80.17. Any PG9933 manufactured after this date will include a sticker indicating compatibility with the IQ Panel 2 Plus.
If you want to check the PowerG Firmware for your IQ Panel 2 Plus, you can do so from the panel. Start from the main screen. Press the small grey bar at the top. Choose Settings > Advanced Settings > enter the Installer Code (default 1111) > About > PowerG. You should check the Radio Firmware Version.
If you have any questions about these incompatibilities, please reach out to us. The best way to contact us is by emailing firstname.lastname@example.org. We will check your email at our earliest convenience and respond back as soon as possible. We look forward to hearing from you.