Revised Qolsys TSB Regarding Update 2.5.2Posted By Michael Goris
Qolsys updated the recent Technical Service Bulletin TSB# 200413 regarding Software Update 2.5.2 for the IQ Panel 2 and IQ Panel 2 Plus. The revised version provides new instructions on successfully performing the update using a Patch Tag. You can view the revised Qolsys TSB here.
In the revised TSB, Qolsys suggests first changing the system Log Level to Verbose, then waiting two (2) minutes, then changing the Log Level to Debug, then waiting another two (2) minutes, then rebooting the panel, and then finally performing the update via a Patch Tag. These new instructions only apply if you are updating the system via Patch Tag. If you have the update pushed down automatically from Alarm.com, then no action is needed.
The previous version of the TSB did not mention waiting 2 minutes, and it did not mention changing the Log Level to Debug. It only said to change the Log Level to Verbose and then perform the update immediately afterward without waiting. We are hopeful that this updated TSB will help end users avoid any confusion or frustration.
In order to change the Log Level, start from the main screen, click the small grey bar at the top, and choose Settings > Advanced Settings > enter the Installer Code or Dealer Code (default 1111 and 2222 respectively) > Installation > System Logs.
Remember you must set the Log Level to Verbose, wait 2 minutes, set the Log Level to Debug, reboot the panel, and then perform the update via patch tag like usual. The reboot can be performed by clicking the grey bar at the top of the screen, and choosing Settings > Advanced Settings > enter IC or DC > Panel Reboot.
The process for updating via Patch Tag involves clicking the small grey bar at the top of the main screen and choosing Settings > Advanced Settings > enter IC or DC > Upgrade Software > Patch Tag > enter iqpanel2.5.2 > OK. The update will then begin. It should take less than 30 minutes for the update to finish. Remember, you must enter iqpanel2.5.2 exactly. The IQ2 must be monitored and connected with a local WIFI network for the update to be performed. It should have its backup battery charged, and the system should be receiving AC power from its plug-in transformer.
If you have any questions about this update, please contact your monitoring company. If you are monitored by Alarm Grid, you may email us at email@example.com for assistance. We check our email from 9am to 8pm ET M-F. We look forward to hearing from you!