Qolsys TSB Regarding PowerG Device Syncing In 2.5.3 and 2.5.4Posted By Julia Ross
Qolsys recently released a Technical Service Bulletin outlining an issue with the IQ2 and IQ2+ panels and PowerG sensors. In some cases, panels that have just installed either firmware version, or panels running these versions that are rebooted, may lose touch with existing PowerG sensors.
The problem, according to Qolsys, is the encryption key. In some rare cases, either during the reboot after the firmware update, or upon rebooting once the firmware update has been applied, the panel's encryption key can be set back to default. Once this occurs, any PowerG devices in the field that have been programmed into the panel will no longer be able to communicate successfully with the panel.
When this situation occurs, a previously working PowerG device will show status on the panel, and on Alarm.com if monitored, of "Not Networked". It may also show an "!" next to the zone's status on the panel's Home Screen. If this condition is allowed to continue for the full supervisory window of the sensor (24-hours for non-life safety sensors, 4-hours for life safety sensors by default) then each affected sensor will go into supervisory failure at the panel and will show a status of Malfunction when viewed through Alarm.com.
If you see this issue on your Qolsys IQ Panel 2 or IQ Panel 2 plus system, you'll need to delete ALL PowerG sensors from the panel, and then re-learn them from scratch. By doing so, a new encryption key will be created and shared with each PowerG device. Once this has been done, all devices should begin working normally again. PowerG devices should be reprogrammed from the panel, not from Alarm.com. This way, full functionality can be verified once programming is complete. It would be best to be sure the panel does not reboot again until the next firmware update, which will resolve this issue. Only PowerG devices are affected by this anomaly, any legacy RF devices using the 319.5MHz, 345MHz, or 433MHz frequencies, and any Z-Wave devices should not be affected by this issue.
If you haven't updated to 2.5.3 or 2.5.4 yet, it is recommended that you update locally at the panel, rather than through Alarm.com. You can find information on updating via Patch Tag or MicroSD card on our Qolsys IQ Panel 2 Plus Firmware Update Page. Sadly, this won't necessarily prevent this issue from happening, but by being onsite at the time of the update, you'll be able to verify proper PowerG sensor functionality on each of your sensors as soon as the update has completed. According to Qolsys, firmware version 2.5.5 will be released in the near future, though an exact date has not been provided. This version will resolve the root cause of this encryption key issue. Any additional future updates will also include the necessary fix.
If you're interested in no-contract, low-cost monitoring, or if you're an Alarm Grid customer (present or future) with questions, you can reach us at firstname.lastname@example.org. We're here to check emails M - F from 9:00 am to 8:00 pm Eastern Time. Thanks for reading, stay safe!